In order to further strengthen the quality supervision and inspection of fire protection products, the fire prevention department of Jinchang detachment and various brigade in-depth jurisdiction over the past few days have conducted comprehensive inspections of fire protection products in the fields of marketing, maintenance and use, and on-site extraction and storage of fire protection products for inspection and effective purification. And regulate the market order of fire products.
During the period, the fire supervision personnel conducted detailed investigations on the stores and maintenance points of fire equipment in the city, and focused on checking whether the three certificates of fire equipment are complete, whether they meet the market access system, and whether the product quality meets the mandatory national standards and industry standards. And local standards, and detailed inspection and registration of product sales records and purchase orders. Aiming at the quality problems of fire products found and illegally selling counterfeit and substandard and unqualified fire products, all fire products sold by them were confiscated, and inspection records of fire products were filled out, and punishments and supervision and rectification were implemented in accordance with the law. And repeatedly reminded the persons in charge of each store and maintenance point to increase awareness of precautions, and do not covet small profits to buy and use fire products that do not meet fire safety standards. At the same time, it explained and publicized how to distinguish the authenticity of fire-fighting products, which strengthened employees' awareness of resisting counterfeit and inferior fire-fighting products. Fire supervisors tell you that the main problems with fire equipment currently on the market are: unqualified filling error of portable fire extinguishers, unqualified hydraulic performance of internal buckle interface, unqualified warp fracture and wear resistance during fire hose burst The performance is unqualified, the water jet strength of the DC water gun is unqualified, the sealing performance is unqualified, the surface quality is unqualified, and the corrosion resistance is unqualified. The unqualified filling error of the fire extinguisher largely reflects that the fire extinguisher manufacturing enterprise is not strictly supervised in the production process and there is a phenomenon of cutting corners and cutting materials. The unsatisfactory hydraulic pressure performance of the internal buckle interface is mainly reflected in the manufacturer's material selection problems and the rubber seal gaskets used in the key seal parts of the interface, which have defects such as pores and cracks, or the elasticity of the seal ring is not ideal, resulting in leakage at the seal part. , Affecting fire rescue. The fire hose failure is mainly due to the single yarn material used by the hose manufacturer failing to meet the design requirements. This may be because the enterprise has lowered the requirements in order to reduce production costs and caused the product to fail. Disqualification of the DC water gun will cause water seepage or even rupture of the water gun, resulting in inability to transport water and affecting fire rescue.
The rectification is mainly aimed at unclear product distribution channels, market access certifications are not consistent, and merchants have taken improper means to sell counterfeit and shoddy products, or have falsely marked on fire products, and falsely filled them with false information to ensure the safety of the source of fire products.
Through the special inspection of fire protection products, it effectively standardized and rectified the market order of fire protection products, improved the quality of fire protection products in areas under its jurisdiction, prevented counterfeit and inferior fire protection products from entering the field of use, enhanced the unit's fire control and disaster prevention capabilities, and eliminated a batch of budding periods. Hidden dangers of fire products. It is reported that the Jinchang City Fire Brigade will continue to carry out in-depth special inspections of fire protection products, severely crack down on counterfeit fire protection products, eliminate potential safety hazards at the source, and take fire protection product inspection and fire prevention and control as long-term key tasks, and resolutely contribute to social fire safety Raise the last line of defense.